£46.62 Ex. VAT
£57.05 Ex. VAT
£61.16 Ex. VAT
£68.95 Ex. VAT
£49.06 Ex. VAT
The Third amendment to BS 7671:2008, The IET Wiring Regulations, became effective on 1 January 2015. Following this, contractors have a six month transition period to get up to speed with the changes and can design, install and certify to either the new or previous standard.
Starting from 1 July 2015 it is a requirement that all electrical installations designed and periodically inspected comply with the updated regulations. Contractors will be expected to hold a copy of BS 7671:2008, incorporating Amendment 3, for any assessment visit taking place after this date.
From the 1st of January 2015, the Regulation 421.1.201 (PROTECTION AGAINST FIRE CAUSED BY ELECTRICAL EQUIPMENT) comes into full effect.
Basically, as of the 1st of July 2015, all electrical installations designed to the new amendment should also be installed to the new amendment and be certified to the 3rd amendment.
The Third amendment recognises UK only regulations and these are now identified by a new numbering system. Regulations with a .100 number are CENELEC requirements and those with a .200 number are specific to the UK.
Part 2 - Definitions - Definitions have been expanded and modified, including the introduction of some new symbols. A list of abbreviations used in the Regulations has been added. The definition of ‘competent person’ has been removed and it has been replaced with ‘instructed person (electrically)’ and ‘skilled person (electrically)’. These changes have been reflected throughout the wiring regulations.
Chapter 41 - Protection against electric shock
There is now a requirement for RCD protection for socket-outlets up to 20A for all installations, however exceptions are permitted for:
Maximum earth fault loop impedances given in tables 41.2, 41.3, 41.4 and 41.6 have been revised to take account of the Cmin factor. Cmin is the minimum voltage factor to take account of voltage variations depending on a number of considerations.
Chapter 42 - Protection against thermal effects
Due to the number of consumer unit fires reported within domestic premises, Regulation 421.1.201 (UK only) has been added and requires consumer units and similar switchgear to have their enclosure manufactured from non-combustible material or be enclosed in a cabinet or enclosure constructed of non-combustible material and complying with Regulation 132.12.
Please note: This regulation will be implemented on 1st January 2016 to allow for manufacturers to ensure an adequate supply of suitable cabinets or enclosures is available.
Chapter 51 - Common rules
Section 551 concerning compliance with standards requires all equipment to be suitable for the nominal voltage and also requires certain information to be noted on the Electrical Installation Certificate.
Chapter 52 - Selection and erection of wiring systems
A new regulation 521.200 (UK only) has been included giving requirements for the methods of support of wiring systems in escape routes.
The regulations concerning selection and erection of wiring systems have been re-drafted. Reference to “under the supervision of a skilled or instructed person” has been removed.
Chapter 55 - Other Equipment
A new section 557 Auxiliary Circuits is included. All auxiliary circuits are defined in Part 2.
Section 559 - Luminaires and lighting installation
Requirements for outdoor lighting installations and extra low voltage lighting installations have been moved to new Sections 714 and 715 respectively.
Part 7 - Special Installations or Locations
Section 701 locations containing a bath or shower There is now a requirement for RCD protection to be provided for:
Appendix 3 - Time/current characteristics of overcurrent protective devices and RCDs
This includes changes in connection with maximum earth fault loop impedance to take account of the Cmin factor given in CLC/TR50480:2011.
Appendix 6 - Model forms for certification and reporting
The schedule of inspections (for new work only) has been replaced by examples of items requiring inspection during initial verifications (which must be appended to the Electrical Installation Certificate).
A small number of changes to the Electrical Installation Condition Report and associated notes have been made, including a requirement to carry out an inspection within an accessible roof space where electrical equipment is present in that roof space.
This summary (found online via BS7671 Amendment 3) is not a definitive guide to all the changes introduced by Amendment 3 and contractors will be required to demonstrate a full and comprehensive understanding of AMD 3 at their assessment visit.
At SparksDirect.co.uk we have a wide range of Consumer Units (both domestic and industrial). The domestic consumer units can no longer be of plastic or flammable material; they have to be of non-combustible material or be enclosed in a cabinet or enclosure constructed of non-combustible material and complying with Regulation 132.12. In general, the consumer units installed after the 1st of January 2016 have to be of ferrous metal (like: steel). All the electrical installations designed after the 30th of June 2015 are to comply with this new amendment to BS 7671:2008, and Regulation 421.1.201 comes into full effect from the 1st of January 2016.
Also, the wiring systems and escape routes are to be supported so that they are not compromised in the case of fire. The main cause for fire is usually a loose connection in a terminal causing a high resistance connection, which then leads to fire. This change to the wiring systems and escape routes is made to improve safety both for the public and for the fire brigade in case of a fire.
Overview of Amendment 3 Changes - Watch a video of the proposed changes in Amendment 3 to BS7671:2008 explained by Mark Coles, Technical Regulations Manager at the IET, takes you through the expected changes to BS 7671 coming in Amendment No. 3 to BS 7671:2008 and the impact that they will have on industry.
Introducing Hager 10 Consumer Units by Steve York, the residential market manager for Hager UK. The Design range of consumer units come in all metal, white finish, with three generous cable entry positions on the back for when the cables come on the back of the boards. Watch this video or see their website for more.
Buy online Amendment 3 Compliant Boards: At Sparks you can find a wide range of Amendment 3 compliant consumer units from 6 way to 20 way, all made of metal and according to the highest specifications to comply with the current regulations. More consumer units are added constantly, click here to see them all.
Sparks Electrical Wholesalers Ltd, 659-661 Holloway Road, Archway, London, N19 5SE, United Kingdom
Registered in England. Company No. 2238028. VAT Reg No: GB 505 6899 17. Copyright © 2003-2019 SparksDirect